- ATEX Certified for use in Hazardous Areas
- Suitable for Zone 1 and Zone 2 areas (gas) and Zone 21 and Zone 22 areas (dusts)
- Widely used in the petrochemical industry
Range & Prices
The prices shown are list prices and perfectly safe to use for budget purposes. Contact your electrical wholesaler for final prices.
|Model||T Class||kW||Voltage||Length||Optional Guard||List Price|
|TXT3-15*||T3||1.5||230V 1ph||2050mm||TXG-01 + TXG-02||£1210.00|
|TXT3-20||T3||2.0||230V 1ph||2650mm||2 x TXG-02||£1396.00|
*Generally available from stock
TXG guards are recommended for installations where personnel have access to heaters. The guards are open ended allowing more than one guard to be used to protect a single heater.
|TXST-01||Wall-Mounted Thermostat 16A T6 (hazardous gas only)||£549.00|
|TXST-02||Wall-Mounted Thermostat 16A T6 (hazardous dust and hazardous gas)||£994.00|
TXST-01 ATEX approved thermostat for use with hazardous gases
TXST-02 ATEX approved thermostat for use with hazardous gases and dusts
(applies to our standard range only)
|Finish||Grey epoxy coating|
|Cable Entry||1 x M20 (gland not supplied)|
|Heating Element||Nickel chrome resistance wire would onto ceramic formers|
|Mounting||Horizontal on wall or floor|
|Fixing Slots||30mm x 10mm at 90˚ to heater length|
|Fixing Slot Centres||Overall heater length – 100mm|
|Voltage Supply||230V 1ph|
|Minimum Ambient Temperature (operating)||-30˚C|
|Maximum Ambient Temperature (operating)||+40˚C|
|Recommended Clearances||105mm from wall
900mm from ceiling
|Equipment Protection Level||Gb (gas) Db (dust)|
|Maximum Surface Temperature||200˚C|
|Zones||Zones 1 and 2 (gas)
Zones 21 and 22 (dust)
|Groups||Group IIC (gas)
|Model||T Class||kW||Length||Weight||Optional Safety Guard|
|TXT3-15*||T3||1.5||2050mm||19.5kg||TXG-01 + TXG-02|
|TXT3-20||T3||2.0||2650mm||24.5kg||2 x TXG-02|
*Generally available from stock
TX ATEX approved heaters installed in a hazardous area
Options Available on Request
Temperature Class T4
Stainless steel 316 construction
Alternative voltages (including 3 phase)
Low temperature operation (-50˚C minimum)
High temperature operation (+60˚C maximum)
- Galvanised steel mesh
- Recommended for installations where personnel have access to heaters.
- Open ended allowing more than one guard to be used to protect a single heater
- Guards should be positioned so that the finned section of the heater is covered. It is not necessary to cover the terminal enclosure
If you would like the experts at BN Thermic to select a suitable heating for your application, please click here to access our enquiry form. Simply provide as much information as you have available and we will respond with a detailed proposal.
Check Suitability of a TX heater for your Area
The following data applies to all standard models in the TX range. Before selecting a specific model you should check that the heater is suitable for the environment. We also suggest that you download and read the TX instructions.
If the standard heaters are not suitable, please contact our Customer Service Department to discuss the options available.
Selecting a Specific Heater
TX heaters are suitable for maintaining background heat or comfort heat in industrial buildings.
In simple terms the output of the TX heater or heaters must be greater than the heat losses from the building during periods of cold weather. A small amount of heat is lost through the walls, ceilings and floors with more significant losses through windows and doors.
To estimate the heat loss from your building you may like to use our heat loss tool
The estimated heat loss figure is the absolute minimum kW output that you should consider installing. We would suggest adding approximately 50% to this figure to allow for an acceptable warm up time in cold conditions as well as making allowances for exceptional weather conditions and possible errors in the original data used in the estimate.
Having established the minimum kW output required, select the minimum number of heaters needed to meet the kW requirement.
The use of TXG safety guards is always recommended where personnel can access the heaters.