- Provides an efficient means of heating industrial premises
- Typical applications include warehouses and workshops
- The most robust unit heater available offering exceptional reliability and backed by a 5 YEAR WARRANTY
- Choice of seven models from 3kW to 25kW all with built in thermostat
- Specially designed bracket for wall or ceiling mounting (heaters also suitable for suspension)
- Multiple heaters can be controlled from a single point if required
Range & Prices
The prices shown are list prices and perfectly safe to use for budget purposes. Contact your electrical wholesaler for final prices.
10kW heater providing background heat in a storage facility in Kent
|Model Number||kW||Voltage||List Price|
|OUH2-03||3.0||230V or 400V/3N||£662.00|
|OUH2-05||5.0||230V or 400V/3N||£679.00|
|OUH2-07||7.5||230V or 400V/3N||£689.00|
Can be wall-mounted or fitted to the rear of a heater
Can control one heater or a chain of heaters.
OUH2 switch can be fitted to a heater. Can be wall mounted if preferred
|Colour:||Light grey case with black grille and bracket|
|Finish:||Epoxy polyester powder coating|
|Construction:||1.2mm steel case|
|Fan:||Motor mounted in cool compartment|
|Thermally protected motor|
|Totally enclosed and factory lubricated fan motor|
|Protection Devices:||High-limit temperature control with automatic reset|
|Heat purge device clears residual heat|
|Heating Element:||Stainless steel sheathed tubular heating element|
|Concentric formation for optimum heat transfer|
|Control:||Factory installed 230V fused control circuit|
|Factory installed contactor|
|Temperature control by means of factory fitted thermostat or choice of remote mounted thermostats.|
|Optional switch (OUH2-S) provides on/off/heat/fan only settings. Can be remote mounted or fitted to the rear of a heater|
|Built-in relays allow a group of heaters to be controlled by a single OUH2-S control switch, thermostat or other controller|
|Installation:||Specially designed bracket for ceiling or wall-mounting provides a variety of discharge angles and 360⁰ rotation|
|Suspension hooks are supplied as standard|
|Maximum recommended mounting height (3kW to 10kW): 2.5m (horizontal discharge), 3m (vertical discharge)|
|Maximum recommended mounting height (15kW to 25kW): 3m (horizontal discharge), 3.5m (vertical discharge)|
|Maximum operating ambient temperature:||30°C|
|Guarantee:||5 year (assuming standard comfort heating application)|
OUH2 installed in a workshop in Billingshurst, West Sussex
|Model||kW||Volts||Airflow (m³/h)||Approximate Temperature
|OUH2-03||3.0||230/1 or 400V/3N||1100||7||60|
|OUH2-05||5.0||230/1 or 400V/3N||1100||13||60|
|OUH2-07||7.5||230/1 or 400V/3N||1100||19||60|
* Noise levels are factory tested, not laboratory tested.
|kW||Height (mm)||Width (mm)||Depth (mm)||Weight (kg)|
|3 to 10||320||435||405||18|
|15 to 25||445||565||485||37|
This is a list of the more frequently requested spare components. Should you require a component that is not listed please contact BN Thermic.
|Part No||Description||Suitable For|
|40001||1kW Heating Element||OUH2-03|
|40003||1.66kW Heating Element||OUH2-05|
|40004||2.5kW Heating Element||OUH2-07|
|40002||3.3kW Heating Element||OUH2-10|
|40005||5kW Heating Element||OUH2-15|
|40006||6.66kW Heating Element||OUH2-20|
|40007||8.33kW Heating Element||OUH2-25|
|80252||Heat Purge Device||All models|
|80254||High Limit Device||All models|
|80250||Factory Fitted Thermostat||All models|
OUH2 Unit heater suspended using hooks provided
OUH2 wall mounted in a warehouse in Axminster, Devon
If you would like the experts at BN Thermic to select a suitable heating for your application, please click here to access our enquiry form. Simply provide as much information as you have available and we will respond with a detailed proposal.
In simple terms the output of the installed OUH2 industrial fan heater or heaters must be greater than the heat losses from the building during periods of cold weather. A small amount of heat is lost through the walls, ceilings and floors with more significant losses through windows and doors.
To estimate the heat loss from your building you may like to use our heat loss tool
The estimated heat loss figure is the absolute minimum kW output that you should consider installing. We would suggest adding approximately 50% to this figure to allow for an acceptable warm up time in cold conditions as well as making allowances for exceptional weather conditions and possible errors in the original data used in the estimate.
Once the target kW has been estimated it is generally as simple as selecting the minimum quantity of heater required to provide that output. Select from the following table.
|OUH2-03||3.0||230V or 400V/3N||1100|
|OUH2-05||5.0||230V or 400V/3N||1100|
|OUH2-07||7.5||230V or 400V/3N||1100|
For perfect heat distribution the combined air volume flow rate of the selected heaters should also be considered. Ideally the total air volume processed by the heaters every hour should be at least four times the total air volume in the building. In some cases therefore, you may choose to select a larger number of lower output heaters in order to increase the total quantity of air processed every hour.
When using OUH2 industrial fan heaters in a building with a roof height in excess of 4m, the installation of a DSU destratification unit is strongly recommended. This device will recycle warm air that has accumulated at high level thereby reducing heating bills by up to 30%. It should also be noted that DSU destratification units provide very high air volume flow rates and often enable the ‘four times total air volume’ target to be achieved without needing to consider additional heaters.