- Fan heaters for direct mounting into a 600 x 600 ceiling grid
- Ideal for heating shops because the heaters do not occupy valuable wall and floor space
- Supplied complete with egg-crate grille
- Optional controller for variable output and fan only settings
For multi-heater installations we recommend SystemX
Range & Prices
The prices shown are list prices and perfectly safe to use for budget purposes. Contact your electrical wholesaler for final prices.
|Model||kW||Volts||Built-in Thermostat||List Price|
An SCH fan heater provides simple and reliable heating in a car service reception area
Heater specifically designed for integration into a suspended ceiling grid
Each heater can be controlled by one wall-mounted controller and/or one thermostat
Do not use room thermostat with ‘T’ suffix models as these heaters already have a built-in thermostat.
|Colour:||Exposed surfaces white RAL9016
Other surfaces zinc plated steel
|Finish:||Epoxy polyester powder coating|
|Construction:||0.9mm steel case
Aluminium air diffuser in brilliant white
|Fan Assembly:||Tangential fan with low noise aluminium fan blades
Shaded pole high performance motor
Factory lubricated bearings (servicing not required)
|Heating Element:||High quality nickel-chrome resistance wire supported by ceramic plates and fitted with an automatically resetting over-temperature device|
|Control (models with built-in thermostat)||
Temperature control by factory fitted electronic thermostat with panel front adjustment
Default mode – built-in thermostat switches heat and fan. This can be changed so thermostat switches heat only with fan running continuously.
Can be controlled by CS-7 wall mounted controller for on/off/high heat/low heat and fan only settings
|Control (models without built-in thermostat)||
Temperature control can be provided by a room thermostat
Can be controlled by CS-7 wall mounted controller for on/off/high heat/low heat and fan only settings. CS-7 can be used in conjunction with a room thermostat
|Installation:||Designed to rest in the T-bar of a 600 x 600 suspended ceiling grid
Recommended mounting heights 2.5m to 4m above floor level (see table below)
|Model||Width (mm)||Depth (mm)||Height (mm)||Required clearance
above grid (mm)
SCH heater installed in a school outfitters
|Model||kW||Volts||Airflow (m³/h)||dB* @2m||Mounting Height (m)|
|SCHG-30(T)||3||230||245||56||2.4 to 3.0|
|SCHG-45(T)||4.5||230||370||60||3.0 to 4.0|
|SCHG-60(T)||6.0||230||490||58||2.4 to 3.0|
* Noise levels are factory tested, not laboratory tested.
This is a list of the more frequently requested spare components. Should you require a component that is not listed, please contact BN Thermic.
|90016||Egg-crate grille (white)|
|AS-SCH-30||Fan/motor/element assembly (3kW) – two used in 6kW heater|
|AS-SCH-45||Fan/motor/element assembly (4.5kW)|
If you would like the experts at BN Thermic to select a suitable heating for your application, please click below to access our enquiry form. Simply provide as much information as you have available and we will respond with a detailed proposal.Enquiry Form
In simple terms the output of the SCH heater or heaters must be greater than the heat losses from the building during periods of cold weather. A small amount of heat is lost through the walls, ceilings and floors with more significant losses through windows and doors.
To estimate the heat loss from your building you may like to use our heat calculation toolHeat Calculator
The estimated heat loss figure is the absolute minimum kW output that you should consider installing. We would suggest adding approximately 50% to this figure to allow for an acceptable warm up time in cold conditions as well as making allowances for exceptional weather conditions and possible errors in the original data used in the estimate.
The next step is to select the output of the heater(s) taking into consideration the height of the suspended ceiling. Use the following table as a guide.
|Model||kW||Built-in Thermostat||Recommended mounting height (m)|
|SCHG-30||3.0||No||2.4 to 3.0|
|SCHG-30T||3.0||Yes||2.4 to 3.0|
|SCHG-45||4.5||No||3.0 to 4.0|
|SCHG-45T||4.5||Yes||3.0 to 4.0|
|SCHG-60||6.0||No||2.4 to 3.0|
|SCHG-60T||6.0||Yes||2.4 to 3.0|
Having established the minimum kW output required and the ouput of the individual heater(s), select the minimum number of heaters needed to meet the kW requirement.