- Stops the accumulation of ice in gutters and downpipes
- Ensures that rain and melt-water can drain away normally and not cause damage to properties
- Reduces risks from collapsing gutters and falling icicles.
Range & Prices
The prices shown are list prices and perfectly safe to use for budget purposes. Contact your electrical wholesaler for final prices.
|GP-18||Self-regulating cable (supplied by the metre)||£21.00|
|THK||Termination kit (one per circuit)||£52.00|
|THJ||Junction Box IP66 6-way terminal block 40A max.||£45.00|
|GP-S||Spacer kit (5 stainless steel spacers and 10 cable ties)||£38.00|
|FST2-EX||Weatherproof Frost Thermostat||£173.00|
|Nominal output at 0°C in ice water:||36W/m|
|Nominal output at 0°C in air:||18W/m|
|Minimum installation temperature:||-40°C|
|Maximum exposure temperature (power on):||60°C|
|Maximum exposure temperature (power off):||85°C|
|Minimum bending radius:||35mm|
|Maximum circuit length:||90m|
- Tin coated copper bus wires
- Self-regulating polymer with bonded jacket
- Thermoplastic insulation
- Tin coated copper earth braid
- UV resistant thermoplastic overjacket
Maximum Length (m) / Circuit Breaker Size (type C)
|Cable||Start-up Temp (˚C)||6A||10A||16A||20A||32A|
If you would like the experts at BN Thermic to select a gutter protection system for you, please send an email to email@example.com with details of your application and we will respond with detailed proposal.
Cable selection for gutters
A single run of GP-18 self-regulating heating cable will protect gutters with widths up to 120mm. For wider gutters add an additional run for every 120mm increase in width. For example a 350mm wide gutter will require 3 runs of cable.
Cable selection for downpipes
For downpipes at the end of a gutter a single run of GP18 self-regulating cable will be required. The cable should extend approximately 500mm below ground level.
For downpipes which interrupt a gutter, a loop of cable should be installed with the end of the loop extending approximately 500mm below ground level.
THK termination kit should be used to prepare one end of the cable for electrical connection and to seal the far end
Electrical connections should be made in a THJ IP66 junction box
A GP-S spacer kit consists of five stainless steel spacers and 10 UV resistant cable ties. The spacers are used to protect the heating cable as it passes over a sharp edge and to maintain the correct spacing when multiple cable runs are installed in a gutter.