- Maintains required temperature in hot water pipes
- Ensures that hot water is instantly available
- Suitable for both domestic and commercial buildings
Range & Prices
The prices shown are list prices and perfectly safe to use for budget purposes. Contact your electrical wholesaler for final prices.
|WM-09||Hot Water Maintenance Cable (supplied by the metre)||£25.00|
|CRJ-T1||Termination kit (one required per circuit)||£20.00|
|THK||Termination kit (one per circuit) uses silicone||£52.00|
|CRJ-S||Splice kit (one required per splice or T joint)||£21.00|
|PF-L||Caution label (10 pack)||£8.50|
|PF-T||Fixing tape 33m x 19mm||£4.00|
|AL-50||Aluminium tape 45m x 50mm (for use with plastic pipes)||£16.00|
|THJ||Junction box IP66 6-way terminal black 40A||£45.00|
|Nominal output at 55°C:||9W/m|
|Minimum installation temperature:||-40°C|
|Maximum exposure temperature (power on):||100°C|
|Maximum exposure temperature (power off):||100°C|
|Minimum bending radius:||30mm|
|Maximum circuit length:||128m|
WM cable maintaining water at a desired temperature
WM hot water maintenance cable is self-regulating. This means that the cables output reduces as the pipe temperature increases and that the cable cannot overheat or burn out.
The cable should be fixed to a water pipe in a straight line and must be covered with insulation. WM can be used with plastic or stainless-steel pipes but these pipes must be wrapped in aluminium tape before the cable is installed.
Insulation Thickness (mm) – Cable should be installed in a straight line under installation
|Maintain Temperature||15mm pipe||22mm pipe||28mm pipe||35mm pipe||42mm pipe||54mm pipe|
Maximum circuit length and breaker size
|Max. Circuit (m)||Breaker (A)|
Selection of Ancillary items
One CRJ-T1 termination kit will be required per circuit. The kit includes the necessary crimps and shrink-on material to prepare one end of the cable for electrical connection and to effectively seal the far end. The kit also includes a nylon gland suitable for making a moisture tight seal into a suitable terminal enclosure.
One CRJ-S1 slice kit will be required for each splice or T joint. . The kit includes the necessary crimps and shrink-on material to join two lengths of cable and to effectively seal the far end.
PF-T fixing tape is supplied in 33m rolls and is ideal for fixing heating cable to the pipe. We recommend securing the cable at 200mm intervals.
When heating a plastic pipe, the pipe should be wrapped in aluminium tape before the heating cable is installed. AL-50 is supplied in 45m x 50mm rolls.
PF-L warning labels are supplied as a pack of 10 and should be fixed to the outside of the insulation at regular intervals.